Maximum outlet pressure: 12 PSI (1.10 BAR)
Maximum flow rate (1): 13 GPM (53 LPM)
Maximum Recommended Viscosity of Pumped Fluid: Diesel Fuel
Maximum ambient operating temperature: 150 °F (66 °C)*
Minimum ambient operating temperature: -15 °F (-26 °C)*
Minimum Dry Vacuum: 6 Inches of mercury
Minimum Suction Lift**: 8 feet for diesel & see below for gasoline***
1) Nominal flow rate at nominal voltage using a standard hose and manual nozzle with low viscosity fluid.
* Consult factory for extreme temperature applications outside this range.
** The lift in feet is equivalent to the vertical distance from the surface of the fluid in the tank to the inlet of the pum
the friction losses through the vertical and horizontal runs of pipe. All elbows and other fittings must be included i
calculation of friction loss. The system should be designed to require a minimum amount of suction lift.
*** Lift of gasoline dependent on Reid's vapor pressure of the gasoline and it's temperature. The lower the vapor
and temperature, the higher the possible lift. Refer to the attached Practical Gasoline Suction Lift Considerations
determine the gasoline lift you can expect.
Phone: (+54) 2983 / 424589 - 434277 - 434425 - Parque Industrial Tres Arroyos (Parcela 12) - Pcia. de Buenos Aires - Argentina